# relai arus lebih overcurrent relay

of 89 /89

Post on 03-Jan-2016

227 views

Category:

## Documents

Embed Size (px)

DESCRIPTION

RELAI ARUS LEBIH OVERCURRENT RELAY. FUNGSI SEBAGAI PENGAMAN UTAMA ATAU CADANGAN UNTUK GANGGUAN HUBUNG SINGKAT FASA – FASA FASA – TANAH APLIKASI PENGAMAN UTAMA JTM ( DISTRIBUSI ) GENERATOR ( Kapasitas kecil ) - PowerPoint PPT Presentation

TRANSCRIPT

FUNGSI

SEBAGAI PENGAMAN UTAMA ATAU CADANGAN UNTUK GANGGUAN HUBUNG SINGKAT FASA – FASA FASA – TANAH

APLIKASI

PENGAMAN UTAMA JTM ( DISTRIBUSI ) GENERATOR ( Kapasitas kecil ) TRAFO DAYA ( Kapasitas kecil ) MOTOR MOTOR BESAR

PENGERTIAN

RELAI ARUS LEBIH

SUATU RELAI YANG BEKERJANYA

ARUS YANG MELAMPAUI NILAI

SETTINGNYA .

JENIS RELAI ARUS LEBIH

• NON DIRECTIONAL• DIRECTIONAL• KONTROL TEGANGAN • PENAHAN TEGANGAN

KARAKTERISTIK

@ ARAH

1. TIDAK BERARAH ( NON DIRECTIONAL )

2. BERARAH ( DIRECTIONAL )

@ ARUS – WAKTU

1. TANPA TUNDA ( MOMENT = INSTANT )

2. TUNDA WAKTU ( TIME DELAY )

# DEFINITE ( TERTENTU ) = INDEPENDEN

# INVERSE ( I – t BERBANDING TERBALIK )

= DEPENDEN

SI / NI = Standard / Normal Iverse

VI = Very Inverse

EI = Exteremely Inverse

LTI = Long Time Invers

IMomentISET

SETt

KARAKTERISTIK INSTANT = MOMENT

t

t

I

SETt

KARAKTERISTIK TUNDA WAKTU TERTENTU ( DEFINITE TIME )

SETI

SETt

KARAKTERISTIK TUNDA WAKTU INVERSE

SETI

INVERSE

KURVA(TMS / Td )

t

I

t

I

SETt

KARAKTERISTIK KOMBINASI INSTANT DENGAN TUNDA WAKTU TERTENTU (DEFINITE TIME )

SETI MomentISET

MomenttSET

t

I

KARAKTERISTIK KOMBINASI INSTANT DENGAN TUNDA WAKTU INVERSE

SETI MomentISET

MomenttSET

SETt

0.6

0.8

1.0

1.2

PEGAS

KONTAK

SETTINGFaktor Pabrik

PLUNGER

BELITAN

INTI LUAR

TIPE PLUNGER

Fe = GAYA ELEKTROMEKANIKFp = GAYA PEGAS

Fe < Fp DROP OFF Fe > Fp PICK UP

Fe

Fp

2

ΦL U2

ΦLU

PIRINGAN

KUMPARAN LAGGING

KUMPARAN UTAMA

TIPE KWH

I

Is

Mempunyai karakteristik Inverse

TAP / PLUG SETING

KUMPARAN UTAMA

TAP SETTING

ARUS DARICT

TIME DIAL SETTING

SETTING ARUS DAN WAKTU

KONTAK DIAM

KONTAK GERAK

DENGAN MENGATURJARAK KONTAK

R

RECTIFIER

SETTING

I

A CT

LEVELDETECTOR

inVoV

RELAIBANTU

SUPLAI DC

TIPE RELAI STATIK

(Reset)0VVV

(Pickup)0VVV

OINREF

OINREF

REFV

MAXI

GATE&

RECT.

FCS

LD1

T LD2

RL

1

R F

LD3 3

RLIsINSTANT

Is

FILTER

CURVESHAPER

LD = LEVEL DETECTORT = TIMERR = REGULATOR

Ia

Ib

Ic

SETTINGINSTANT

BLOK DIAGRAM RELAI ARUS LEBIH STATIK

IBA DOC

0.2/0.10.2/0 0.4/0

0.8/00.4/0

A/D

OUTPUTDRIVER

MICROCOMPUTER

16/0

8//0

4//0

2/0

1/0

0.4/0

0.2/0

0.2/0

0.1/0

0.05/0

0.05/0.025

CURVE SELECT SWITCH

HIGH SET SWITHSETTING

TMS SWITH SETTING

TIMEHS

HS OUTPUTRELAY

TIME / CURRENTOUTPUT RELAY

FULLWAVERECTIFIERINTERPOSSING

CT

INPUT

CURRENT SETTING

STATIC OVER CURRENT RELAYMCGG

IBA DOC

A B C EINST

tI > Is

INST

tI > Is

NAMEPLATE

RESET

KARAKTERISTIK

NS II

xt

Is

I INST

Is

I INST

xt

NS II

RELAIOCR / GFR

TIPEMCGG 82

IBA DOC

PRINSIP/CARA SETTING OCR

# Iset Tunda waktu ( I > /Io>)

* Is = k In In = Arus Nominal k = Faktor pabrik ( 1 s/d 2 ) atau 0,05 s/d 2,4 dengan step 0.05

* Plug Setting * Numeric

IBA DOC

# Waktu kerja (t> / to> )

* Definite ( Langsung atau dengan Tms ) * Inverse ( Td atau Tms dan Mps = I / Is )

Tms ( td )

x IsMps = 4 x Is

t

tk

Td = Time dial settingTms = Time multiple setingMps = Multiple plug setting …. X Is

IBA DOC

1,0

0,6

tk

# Is instant /moment ( I>> / Io>> )

* Is instant = k In atau k Is In = Arus Nominal Is = Arus setting tunda waktu k = Faktor pabrik

* Plug setting

* Numeric

IBA DOC

@ SETTING ARUS OCR /GFR DENGAN TUNDA WAKTU

N

S

NS

I

I

II

ARUS SETTING

ARUS NOMINAL RELAI

FAKTOR PABRIK

0.10.1

0.2

0.4

0.4

0.4

0.8

0.050

00

0

0

0

IBA DOC

CONTOH CARA SETTING DENGAN MENGGUNAKAN OCR / GFR TIPE MCGG82

0.10.1

0.2

0.4

0.4

0.4

0.8

0.050

00

0

0

0

# MISAL ARUS SETTING Is = 6 A. Is = 1.2 In

POSISI SAKLAR :

Is = ( 0.1 + 0.1 + 0.2 + 0 + 0 + 0 + 0.8 ) x 5A = 1,2 x 5A = 6 A

IBA DOC

PEMILIHAN KARAKTERISTIK

SI VI EI LTI D2 D4 D8

0 1 0 1 0 1 0

0 0 1 1 0 0 1

0 0 0 0 1 1 1

101

11

000

1

100

TRIP TEST : CURVA SI :

IBA DOC

KURVA / KARAKTERISTIK

@ STANDARD / NORMAL INVERSE ( SI )

tmsI

t1

14,002,0

@ VERY INVERSE ( VI )

tmsI

t1

5,13

@ EXTREMELY INVERSE ( EI )

tmsI

t1

802

@ LONG TIME INVERSE ( LTI )

tmsI

t1

120

IBA DOC

SETTING WAKTU

MISAL : KARAKTERISTIK EI ARUS GANGGUAN 3 x Is ( I = 3 )

WAKTU KERJA = 1 DETIK PEMILIHAN TMS :

0,11

80

13t

80

1Itms

2

k

2

POSISI SAKLAR 0,025 0,050,050,10,20,20,4

00

000

IBA DOC

SETTING INSTANT

SS

S

S

IinstI

36

18

6AI

18AinstI POSISI SAKLAR

24

1

816

000000

IBA DOC

X

P1

P2

50 / 51 51N

300/5A10P1530VA

20KV

DATA SETTINGI> = 5A; Io> = 1A ; I>> = 35At>=0,5 detik ;to>=0,5 detikKarakteristik tunda waktu = SI

F

Ihs3f=3300AIhs2f=2000AIhs!f= 210A

In relai = 5A

Io>> tdk aktip

TMSSETTING

INSTSETTING

CURVESELECTION

Is PhA

μC

<<<<

<<

INPUTCIRCUIT Ph

CURRENTSETTING Ph

TMSSETTING

INSTSETTING

CURVESELECTION

Is PhB

μC

<<

<<

<<

INPUTCIRCUIT Ph

CURRENTSETTING Ph

TMSSETTING

INSTSETTING

CURVESELECTION

Is PhC

μC

<<

<<

<<

INPUTCIRCUIT Ph

CURRENTSETTING Ph

TMSSETTING

INSTSETTING

CURVESELECTION

Is E/F

μC

<<

<<

<<

INPUTCIRCUIT E/F

CURRENTSETTING E/F

OUTPUTCIRCUIT Ph

OUTPUTCIRCUIT E/F

2

1R L

2

2R L

2

3R L

2

4R L

POWERSUPPLYCIRCUIT

TIME DELAY TRIP

INST TRIP

TIME DELAY TRIP

INST TRIP

TIME DELAY TRIP

INST TRIP

INST TRIP

TIME DELAY TRIP

INDICATORRESET

36

13

14

RL 1-1

RL 1-2

35

3334

29

30

37

41

38

7

42

RL 2-1

RL 2-2

RL 3-1

RL 3-2

6

2

5

1

8

109

16

15

44

21

22

24

23

27

26

25

28

49

50

48

47

45

46

43

RL 4-1

RL 4-2

+- Vx

PHASE FAULTTIME DELAYEDTRIP OUTPUT CONTACT

PHASE FAULTINSTATANEOUSTRIP OUTPUT CONTACT

EARTH FAULTINSTATANEOUSTRIP OUTPUT CONTACT

EARTH FAULTTIME DELAYEDTRIP OUTPUT CONTACT

AI

BI

CI

NI

MCGG 82

RS

TE

CT

P1

P2

S1

S2OCR

OCR

GFROCR

SAMBUNGAN ( WIRING )

PMT

IBA DOC

Diagram AC

Sambungan tipe 3 OCR + 1 GFR

R

TE

PMT

CT

P1

P2

S1

S2OCR

OCRGFR

IBA DOC

Sambungan tipe 2 OCR + 1 GFR

Diagram AC

PENGUJIAN RELAI ARUS LEBIH

1. PENGUJIAN INDIVIDUAL MENGUJI INDIVIDU RELAI ITU SENDIRI , UNTUK

MENGETAHUI APAKAH MASIH DALAM KEADAAN STANDAR ATAU TIDAK

2. PENGUJIAN FUNGSI

MENGUJI FUNGSI DARI SISTEM PROTEKSI SECARAKESELURUHANAPAKAH MASIH BERFUNGSI ATAU TIDAK

PENGUJIAN INDIVIDUAL

HAL HAL YANG PERLU DIPERHATIKAN :

1. CARA SETTING 2. INTERNAL DIAGRAM RELAI3. ALAT UJI / RANGKAIAN PENGUJIAN4. ITEM PENGUJIAN 5. PROSEDUR PENGUJIAN6. HASIL UJI DAN KESIMPULAN

JENIS / ITEM PENGUJIN

1. ARUS PICK UP DAN ARUS DROP OFF SERTA RASIO ARUS PICK UP DENGAN DROP OFF

2. KARAKTERISTIK ARUS – WAKTU

3. KARAKTERISTIK INSTANTANEOUS

1. ARUS PICK UP [ ARUS AWAL / MULA ] ARUS MINIMUM YANG MENYEBABKAN RELAI BEKERJA

2. ARUS DROP OFF [RESET/ KEMBALI ] ARUS MAKSIMUM YANG MENYEBABKAN RELAI TIDAK BEKERJA.

3. RASIO ARUS PICK UP DENGAN DROP OFF

100%I

IK

P

dd

I

t

I pick up

I reset

I beban

t gangguan

PENGUJIAN INDIVIDUAL RELAI ARUS LEBIH

A

220 Vac

220 Vac

TIMER

START STOP

R

TRAFO ISOLASISLIDE

RANGKAIAN PENGUJIAN

21

22

23

242526

27

28

29

30

13

14 Vdc

220 VVOLTMETERCT SECC2 C1 C0P1 P2T1 T21 2

MAKE

BREAK

OFF

TIME

LAMP

A SELECTOR

POWER

ON

OFF

OFFFAULT

ON

B B A

OCRUCR

OVRUVR OTHER

RELAY

TEST CONDITIONMIN MAXMIN MAXOFF 1 A

5 A10 A

75 V

300V

150V

B SELECTOR

AV A

ON

OFF

EXT

INT

PORTABLE TEST SET RELAY TIPE TPR 22 CV

220 VVOLTMETERCT SECC2 C1 C0P1 P2T1 T21 2

MAKE

BREAK

OFF

TIME

LAMP

A SELECTOR

POWERON

OFF OFFFAULT

ON

B B A

OCRUCR

OVRUVR OTHER

RELAY

TEST CONDITIONMIN MAXMIN MAXOFF 1 A

5 A10 A

75 V

300V

150V

B SELECTOR

AV A

ON

OFF

EXT

INT

16

21

22

23

24

25

26

27

28

13

14

+-A

B

C

E/F

MCGG 82

OCR / GFRYANG DIUJI

30

41

42

29

2

1

15

RANGKAIAN PENGUJIAN OCR/GFR DENGAN ALAT UJI TPR 22 CV

IBA DOC 2003

24

23

25

26

13

14

RELAI OCR / GFR MCGG 82

ALAT UJIXS92a ABB

HAND TERMINAL

RANGKAIAN PENGUJIAN RELAI OCR / GFR TIPE MCGG 82

PENGUJIAN RELAI OCR /GFR MCGG 82

27

21

28

22

42

41

1

2

16

29

15

30t >

t >>

to>

to >>

+-

Vx

(+)

(+)

(+)

(-)

(-)

KONTAKOCR/GFR

RELAIBANTURE 1

RE 2

RELAIBANTURE 3

ALARM

TRIP PMT

DIAGRAMKONTROL DCPROTEKSIOCR/GFR

(+)

RESET

TEST LAMP

RELAI BANTU RE

LAMPUSIGNAL

KONTAKRELAI

DIAGRAM SIGNALISASI

xQ1630A

MWH MWHA

TO METERINGREMOTE CONTROLPANEL

V

F3MVTR5179

200 – 400/1A,30VA,10P20

200 – 400/1A,15VA,0,5

T1-3

T1-3

Q2

HL1-3

0,3A

fu1-3

S6

P2

P3-1 P3-2

OUTIN

x5

x3x4

F2F1

MCGG2250G/51G

MCGG5250 / 5150G/51G

T5

T5

20KV/V3100V/V3

125VA,CL 1,0

3PH,20KV,2500A,50Hz,25KA,3Sec

Grounding Neutral Bar 2000a

SINGLE LINE DIAGRAM FEEDERSCHEMATIC TYPE C2

LEGEN

F1

F2

F3

PL1-3

P2

P31-2

S6

X3-X4

X5

HL1-3

Over Current & Earth Fault Relay

Grounding Phase Detecting Relay

Auto Recloser Relay

Ammeter double scale 0 – 200/400/1A

KV meter 20KV / 100V

MWHmeter In - Out

Selector Switch Volt 4 Position

Current Test Blick

Potential Test Block

Neon Voltage Indicator

SYMBOL

PL1-3

I >>

I >

Io >>

Io >

22

2930

34

33

35

42 41

38

37

36

1 2

5

6

7

15 16

9 810

Io >>

1 2

5

6

7

15 16

9 810

Io >

13

14

1413

110VDC

+T

-T

28

27

27 28

25 26

21

MCGG52 MCGG22

F1F2

X4

TLB

XB3

TERMINAL

1

2

3

4

2 2

03 3

04 4

01 1

P1

L1 L2 L3

P1

P1

2S3

2S12S2

2S2

2S1

2S3

2S1

2S22S3

T3

T1

T2

POWER CIRCUIT PROTECTIONFEEDER SCHEMATIC

200 – 400 / 1A30VA,10P20

X

M

LOCAL REMOTE

CLOSE OPEN0CB

S8

S3

+C

+T

M

N

-T

- C

Q1 KN

YL

YB

OPEN

CLOSE

1

2

3

4

5

6

K415/8

CL

OS

E

OP

EN

FROM RCPPANEL

3

4

K315/6

1

2

3

4

3

4

3

4

1

2

F2F1 F1 F1 F1 F2

5

7 7

534

35

8

99

8

36

38

FROM BUCHOLZ

TRIPPINGORDERFACILITY

CIRCUIT BREAKERCONTROL FEEDERSCHEMATIC

1

2S17/4

S17/4

5

6

IBA 2006

I >>

I >

Io >>

Io >

22

2930

34

33

35

42 41

38

37

36

1 2

5

6

7

15 16

9 810

Io >>

1 2

5

6

7

15 16

9 810

Io >

13

14

1413

110VDC

+T

-T

28

27

27 28

25 26

21

MCGG52 MCGG22

F1F2

X4

TLBXB3

TERMINAL

1

2

3

4

02 2

03 3

04 4

01 1

P1

L1 L2 L3

P1

P1

2S3

2S12S2

2S2

2S1

2S3

2S1

2S22S3

T3

T1

T2

200 – 400 / 1A30VA,10P20

TEST SETINJEKSI SEKUNDER

RANGKAIAN PENGUJIAN FUNGSI

SETTING OCRGANGGUAN FASA – FASA [ TUNDA WAKTU

max.-beban-arusI

80%k

1,21,1k

maxIIminImaxI

minIImaxIminI

min....[2]0,8ImaxI

.....[1]k

IkminI

max

D

S

SETSETSETSET

SETSETSETSET

HS2ΦSET

D

maxSSEI

KOORDINASI OCR

# DEFINITE TIME

A B C

t

I

0,3 det

0,8 det

1,3 det

0,5det0,4Δt

ttt

IIII

ABC

HSSASBSC

KOORDINASI OCR

# INVERSE TIME

A B C

t

I

TMS ATMS B TMS C

SETING WAKTU DENGAN PEMILIHAN TD / TMS TD = TIME DIAL TMA = TIME MULTIPLE SETTING

SETTING ELEMEN INSTANTANEOUS

DIMAKSUDKAN UNTUK GANGGUAN 3 FASA ,TETAPI HARUSMEMPERHATIKAN ARUS KETAHANAN KABEL .

kabel-kemampuanSET2

HS3ΦSET1HS2Φ

II

minIIminI

SETTING INSTANT

SET2SETSET1SET2

SET1SETSET2SET1

IIII

IIII

KOORDINASI OCR

# INSTANTANEOUS

A B C

C1,2.Iinst.BI

B1,2.Iinst.AI

HS3ΦSET

HS3ΦSET

KOORDINASI DARI RELAI KOMBINASI TUNDA WAKTUDENGAN INSTANT /

A B C

t

I

TMS ATMS B TMS C

t

I

t A

t B

t Ct INST t INST

t INST t INST

SETTING GFR[RELAI GANGGUAN TANAH ]

PERLU DIPERHATIKAN ;

1. SISTEM PENTANAHAN TITIK NETRAL2. BESARNYA ARUS HUBUNG SINGKAT SATU FASA KE TANAH .3. ARUS KETIDAKSEIMBANGAN BEBAN4. ARUS KAPASITANSI JARINGAN .

SISTEM PENTANAHAN DENGAN TAHANAN RENDAH

3 PADA SKTM SPINDEL BATAS MINIMUM ADALAH RELAI PADA SALURAN YANG SEHAT TIDAK BOLEH BEKERJA OLEH ARUS KAPASITANSI ORI3

ORSET IGFRI 33,1

# PADA SUTM SAMA SEPERTI DI SKTM

@ SISTEM PENTANAHAN LANGSUNG [ SOLID ]

KARENA ARUS GANGGUAN BESAR , KRITERIA SETTINGNYA SEPERTI PADA RELAI PENGAMAN ANTAR FASA . TETAPI BATAS MINIMUMNYA LEBIH KECIL DARI ARUS BEBAN , TETAPI LEBIH BESAR DARI ARUS KETIDAKSEIMBANGAN BEBAN .

@ SISTEM MENGAMBANG

1. RELAI TEGANGAN NOL RELAI INI TIDAK BOLEH BEKERJA BILA TERJADI PERGESERAN TEGANGAN NOMINAL

2. RELAI GANGGUAN TANAH BERARAH [ DIRECTONAL GFR ]

@ SISTEM PENTANAHAN DENGAN TAHANAN TINGGI

RELAI YANG DIGUNAKAN ADALAH DGFR . RELAI OCR SEBAGAI GFR TIDAK DAPAT DIPAKAI . KARENA ARUS GANGGUAN SATU FASA KETANAH LEBIH KECIL DARI ARUS KAPASITANSI .

NomO VV 3,03

220 VVOLTMETERCT SECC2 C1 C0P1 P2T1 T21 2

MAKE

BREAK

OFF

TIME

LAMP

A SELECTOR

POWER

ON

OFF

OFFFAULT

ON

B B A

OCRUCR

OVRUVR OTHER

RELAY

TEST CONDITIONMIN MAXMIN MAXOFF 1 A

5 A10 A

75 V

300V

150V

B SELECTOR

AV A

ON

OFF

EXT

INT

PORTABLE TEST SET RELAY TIPE TPR 22 CV

220 VVOLTMETERCT SECC2 C1 C0P1 P2T1 T21 2

MAKE

BREAK

OFF

TIME

LAMP

A SELECTOR

POWERON

OFF OFFFAULT

ON

B B A

OCRUCR

OVRUVR OTHER

RELAY

TEST CONDITIONMIN MAXMIN MAXOFF 1 A

5 A10 A

75 V

300V

150V

B SELECTOR

AV A

ON

OFF

EXT

INT

16

21

22

23

24

25

26

27

28

13

14

+-A

B

C

E/F

MCGG 82

OCR / GFRYANG DIUJI

30

41

42

29

2

1

15

RANGKAIAN PENGUJIAN OCR/GFR DENGAN ALAT UJI TPR 22 CV

IBA DOC 2003

24

23

25

26

13

14

RELAI OCR / GFR MCGG 82

ALAT UJIXS92a ABB

HAND TERMINAL

RANGKAIAN PENGUJIAN RELAI OCR / GFR TIPE MCGG 82

PENGUJIAN RELAI OCR /GFR MCGG 82

27

21

28

22

42

41

1

2

16

29

15

30t >

t >>

to>

to >>

+-

Vx

PROSEDUR PENGUJIAN

PARAMETER

FR = 50DFR= 0DF = 0FC = SESUAI JENIS GANGGUANSQ = PU / DROPA = SQ = 2IRA = 0 A = 0TO = 100 AUTOTL = 100 SQ = 1F0TF = > t set A = 1IN1 = 1IN2 = 0OU1= 0/1OU2= 0TI = 2TT = 0MOD= UIMT = 1OP = 0

UI

U = 57 VI = . . . APHI= 90

DU = 0DI = 0,01DPH=0LUH = 220LUL = 0LIH = 20ALIL = 0LPI =359LPO = 0UJI PU / DROP OFF

START + / -Sambungan ke kontak dilepas

Uji waktu kerja [ sambunganke kontak dipakai]START +

0 2X ENTER

FC = CODE GANGGUAN

111 = R KE E112 = S KE E113 = T KE E

121 = GANGGUAN R S 122 = GANGGUAN ST 123 = GANGGUAN TR

I>/In

RESETSTEP

PROGRAM

t> [s]kI>>/Int>> [s]kIo>/Into> [s]koIo>>/Into>> [s]ko

SGB

SGF

SGRTRIP

SPAJ 140 C

80. . . 265 V dc/ac18. . . .80V dc

L1 L2 L3 Io IRF

OPER. IND

1. I> start 2. I> trip 3. I>> start 4. I>> trip 5. Io> start 6. Io> trip 7. Io>> start 8. Io>> trip 9. CBF

00 0 0 0

REGISTER

1. IL1/In2. IL2/In3. IL3/In4. Imax5. t(I>)[%]6. t(I>>) [%]7. Io/In8. t(I0>) [%]9. t(Io>>)[%]

1

2

3

4

5

6

7

8

KETERANGAN GAMBAR :

1. Lampu indikator Phase yang terganggu . L1 menyala artinya phase R terganggu L2 menyala artinya phase S terganggu L3 menyala artinya phase T terganggu Io menyala artinya ada gangguan tanah.

2. Display Monitor : untuk indikator besarnya setting arus ; waktu dan indikator kerja .

* * * * Display Indikator besarnya arus sekunder( I> , I>> , Io> , Io>> ) serta setting waktu( t> / k> , t>> / k>> , to> / ko > , to>> / ko >> )Untuk melihat setting tekan tombol (3) akan Muncul indikator besarnya setting.

Display indikator kerja, bila indikator muncul angka sbb :1. I> start ( OCR )2. I> trip ( OCR )3. I>> start OCR Moment / Instant )4. I>> trip ( OCR Moment / Instant )5. Io> start ( GFR )6. Io> trip ( GFR )7. Io>> start ( GFR Moment / Instant )8. Io>> trip ( GFR Moment / Instant )

3. Tombol Reset / Step a. berfungsi sebagai reset indikator kerja relai. b. berfungsi sebagai perubah step setting arus dan waktu bila difungsikan.

4. Tombol Program berfungsi untuk memprogram setting arus dan waktu sesuai setting yang diinginkan.

5. Lampu indikator trip ( warna merah ) Bila relai merasakan arus gangguan sampai t set ( setting waktu relai ) tercapai. Maka lampu indikator 5) akan menyala.

6. Lampu indikator setting arus dan waktu yang diinginkan.

7. Keterangan dari Display indikator kerja relai 2).

8. Lampu indikator untuk menunjukan bahwa tegangan dc di relai telah tersedia.

UI3I>

3I>

Io>

Io>>

AC Setting Reset

5A 1A 5A 1A 5A 1A 5A 1A

U1/

SGR

3/1

U1/

SGR

3/2

U1/

SGR

3/3

U1/

SGR

3/4

U1/

SGR

3/5

U1/

SGR

3/6

U1/

SGR

3/7

U1/

SGR

3/8

U1/

SGR

1/1

U1/

SGR

1/3

U1/

SGR

1/5

U1/

SGR

1/7

U1/

SGR

2/1

U1/

SGR

2/3

U1/

SGR

2/5

U1/

SGR

2/7

U1/

SGR

2/2

U1/

SGR

2/4

U1/

SGR

2/6

U1/

SGR

2/8

SGB6SGB7

U1/

SGR

1/2

U1/

SGR

1/4

U1/

SGR

1/6

U1/

SGR

1/8

U1/SGB1

U1/SGB2

U1/SGB3

U1/SGB4

U1/SGB5

U1/SGB8

U2

U3

1 2 3 64 5 257 8 9 26 27

U1/SGF4

0,1…1s

T9

T1

T3

T5

T7T8

T6

T4

T2

TRIP

SS3 TS2TS1 SS1 SS2

ABCDEF

6665

+TRIP

Rx

Tx

69688180787775747170 7262 611011

IRF START 2START 1 SIGNAL 1 SIGNAL 2

r s tn Io

Uaux

63

11 1 1 1

Internal diagram relai OCR / GFR SPAJ 140 C

SGR1/8

SGR2/8

SGR2/7

SGR3/8

SGR1/7

SGR3/7

SGR1/6

SGR2/6

SGR2/5

SGR3/6

SGR1/5

SGR3/5

SGB3

SGB4

SGB6

SGB5

>Io >>

>Io > to> ko

to>>

SGB1

SGB2

IL3

IL1IL2

BS

Io

>I >> t>>

>I > t> k

SGR3/4

SGR1/4

SGR2/4

SGR2/3

SGR2/7

SGR1/3

SGR3/3SGR1/2

SGR2/2

SGR2/1SGR3/2

SGR1/1

SGR3/1

>

1

SGB/7

RESETPROGRAM

>

1

SGB/6

RESETPROGRAM

1

> RESET

1

SGF1/4

SGF2/8

0,1..1S1

AR1

AR2

AR3

TS1

SS2

SS3

SS1

TS2

IRFIRF

F

E

D

START 1

START 2

SIGNAL 1C

SIGNAL 2B

TRIPA

SPTU R1REDUCED BLOCK DIAGRAM SPCJ 4D 29

REMOTE SETTING

RELAY RESET

CONTROL SIGNAL ANTAR MODUL SPAJ 140 C

TRIP

CEK MULA OCR/GFR SPAJ 140 C

1. Setelah relai disambung ke Aux. supply dc , melalui terminal relai nomer 61 [+] dan 60 [-] , sesaat kemudian lampu indikator U aux. menyala dan display menyala per segmentnya, kemudian display akan padam .2. Kemudian cek lampu indikator Trip, caranya sebagai berikut : # tekan tombol push botton STEP RESET sehingga display menunjuk seperti gambar di bawah ini .

STEPRESET

n x 1s 0 0 0 0

# kemudian tekan push botton PROGRAM kira kira 5 detik sampai display menunjuk seperti gambar dibawah ini.

PROGRAM

5s 0 0 0 0

I>/Int> [s]kI>>/Int>> [s]kIo>/Into> [s]koIo>>/Into>> [s]ko

SGB

SGF

SGRTRIP

PROGRAM

1s 0 0 0 0

# kemudian tekan tombol push botton PROGRAM kira kira 1 detik sampai display menunjuk seperti gambar dibawah ini ( lampu indikator t>, t>>, to>, to>> menyala )

# kemudian tekan tombol push botton STEP/RESET dan PROGRAM secara bersamaan ,maka lampu indikator TRIP akan menyala dan display menunujuk seperti dibawah ini ( berarti oke )

PROGRAM

0 0 0 0

RESETSTEP

1s

I>/Int> [s]kI>>/Int>> [s]kIo>/Into> [s]koIo>>/Into>> [s]ko

SGB

SGF

SGRTRIP

RESETSTEP

PROGRAM

I>/Int> [s]kI>>/Int>> [s]kIo>/Into> [s]koIo>>/Into>> [s]ko

SGB

SGF

SGRTRIP

RESETSTEP

PROGRAM

3. Dengan kondisi display seperti dibawah, kemudian tekan tombol push botton RESET / STEP maka lampu indikator IRF akan menyala .

RESETSTEP

1s 0 0 0 0

I>/Int> [s]kI>>/Int>> [s]kIo>/Into> [s]koIo>>/Into>> [s]ko

SGB

SGF

SGRTRIP

RESETSTEP

PROGRAM

IRF

PROGRAM SWITCH GROUP SGF, SGB, SGR

1. SGF (Switch Group for Function) SGF terbagi atas dua bagian yaitu : 1.1. SGF 1 1.2. SGF 21.1. SGF1 terbagi atas 8 bagian sebagai berikut : SGF1/1 SGF1/2 SGF1/3

SGF1/1 SGF1/2 SGF1/3 Mode operasi Karakteristik 0 0 0 definite time 0,05 ….. 300s 1 0 0 IDMT Extremely inverse 0 1 0 idem Very inverse 1 1 0 idem Normal inverse 0 0 1 idem Long time inverse 1 0 1 idem karakteristik R I 0 1 1 idem karakteristik RX1DG 1 1 1 tidak digunakan

Dipakai untuk menentukan / memilih karakteristikkerja dari I > yang diinginkan

SGF1/4 dipakai sebagai Breaker Faillure Protection (CBF) atau tidak

SGF1/5 dipakai untuk melipat gandaka nilai setting I >> secara otomatis bila dipasang pada level inrush current.

SGF1/6SGF1/7SGF1/8

Dipakai untuk memilih karakteristik kerja dari Io> yangdiinginkan.

SGF1/1 SGF1/2 SGF1/3 Mode operasi Karakteristik 0 0 0 definite time 0,05 ….. 300s 1 0 0 IDMT Extremely inverse 0 1 0 idem Very inverse 1 1 0 idem Normal inverse 0 0 1 idem Long time inverse 1 0 1 idem karakteristik R I 0 1 1 idem karakteristik RX1DG 1 1 1 tidak digunakan

1.2. SGF2 terbagi atas 8 bagian sebagai berikut : SGF2/1 SGF2/2 SGF2/3 SGF2/4

SGF 2/5 dipakai untuk mengaktipkan atau tidak arus Moment ( I>> ) SGF2/6 dipakai untuk mengaktipkan atau tidak arus Moment gangguan tanah ( Io>> ) SGF2/7 dipakai untuk mengaktipkan atau tidak recloser (bila diperlukan , input dari signal starting I> / I>> ). SGF2/8 dipakai untuk mengaktipkan atau tidak recloser ( bila diperlukan, input dari signal starting Io> / Io>> ).

Dipakai untuk mereset secara manual atau otomatiDari indikator starting I > / I>> / Io> /Io>>.

2. SGB ( Switch Group for Blocking ) SGB1/1 SGB1/2 SGB1/3 SGB1/4 SGB1/5 saklar ini memungkinkan merubah dari setting utama ke

setting ke dua dan sebaliknya tanpa komunikasi, menggunakan input signal external control BS

SGB1/6 untuk memilih sebuah penghalang untuk signal tripping

TS2 untuk gangguan phase. SGB1/7 untuk memilih sebuah penghalang untuk signal tripping

TS2 untuk gangguan tanah. SGB1/8 Resetting secara remote ( jarak jauh ) sebuah penghalang

output relai.

Dipilih bila external control signal BS digunakan untuk memblokir satu atau lebih dari tingkatan arus dari modul.

3. SGR (Switch Group for Relay Configuration) SGR ini terbagi ke dalam 3 bagian yaitu : 3.1. SGR1 3.2. SGR2 (stage – 2 ) 3,3. SGR3

3.1. SGR1 Saklar ini digunakan untuk memilih tingkatan proteksi yang dibawa ke output signal starting SS1 dan output signal tripping TS2 .

SGR1 ini terbagi atas : SGR1/1 untuk signal starting tingkat I> disambung ke SS1 ( terminal relai

nomer 77 – 78 ). SGR1/2 untuk signal tripping tingkat I> disambung ke TS2 ( terminal relai nomer 65 – 66 ). SGR1/3 untuk signal atarting tingkat I>> disambung ke SS1 ( terminal 77 – 78 ). SGR1/4 untuk signal tripping tingkat I>> disambung ke TS2 ( terminal 65 – 66 ). SGR1/5 untuk signal starting tingkat Io> disambung ke SS1 ( terminal 77 – 78 ). SGR1/6 untuk signal tripping tingkat Io> disambung ke TS2 ( terminal 65 – 66 ). SGR1/7 untuk signal starting tingkat Io>> disambung ke SS1 ( terminal 77 – 78 ). SGR 1/8 untuk signal tripping tingkat Io>> disambung ke TS2 ( terminal 65 – 66 ).

3.2. SGR2 Saklar ini dipakai untuk konfigurasi signal tripping tingkat proteksi yang berbeda . Mempunyai dua output SS2 dan SS3 yang mana signal dapat disambung. SGR2 ini terbagi atas : SGR2/1 untuk signal starting tingkat I> disambung ke SS2 ( terminal relai no 80 – 81 ) SGR2/2 untuk signal tripping tingkat I> disambung ke SS3 ( terminal relai no 68 – 69 ) SGR2/3 untuk signal starting tingkat I>> disambung ke SS2 ( idem SGR2/1 ) SGR2/4 untuk signal tripping tingkat I>> disambung ke SS3 ( idem SGR 2/2 ) SGR2/5 untuk signal starting tingkat Io> disambung ke SS2 ( idem SGR 2/1 ) SGR 2/6 untuk signal tripping tingkat Io> disambung ke SS3 ( idem SGR 2/2 ) SGR2/7 untuk signal starting tingkat Io>>disambung ke SS2 ( idem SGR 2/1 ) SGR2/8 untuk signal tripping tingkat Io>> disambung ke SS3 ( idem SGR 2/2 )

3.3. SGR 3. Saklar ini dipakai untuk konfigurasi signal starting dan tripping untuk output starting atau auxiliary tripping TS1 Catatan : Jika proteksi CBF (Circuit Breaker Failure ) dipilih pada SGF 1/4 ,ini juga menggunakan output TS1. SGR3 terbagi atas { SGR3/1 untuk signal starting tingkat I> disambung ke TS1 ( terminal relai nomer 74 – 75 ) SGR3/2 untuk signal starting tingkat I> disambung ke TS1 ( idem SGR3/1 ) SGR3/3 untuk signal starting tingkat I>> disambung ke TS1 ( idem SGR3/1 ) SGR3/4 untuk signal starting tingkat I>> disambung ke TS1 ( idem SGR 3/1 ) SGR3/5 untuk signal starting tingkat Io> disambung ke TS1 ( idem SGR3/1 ) SGR3/6 untuk signal starting tingkat Io> disambung ke TS1 ( idem SGR3/1 ) SGR3/7 untuk signal starting tingkat Io>> disambung ke TS1 ( idem SGR3/1 ) SGR3/8 untuk signal starting tingkat Io>> disambung ke TS1 ( idem SGR 3/1 ).

CARA SETTING ( PEMROGRAMAN )

Setelah CEK MULA item 1. dilakukan ,kemudian lakukan Penyetelan pada :

1. SGF 1 (Switch Group of Function ) SGF1/1 SGF1/2 SGF1/3

Untuk menentukan karakteristik waktu ,misal kita pilih adalahDefinite time maka :SGF1/1 diset = 0SGF1/2 diset = 0SGF1/3 diset = 0

CARANYA :a) Tekan push botton STEP-RESET sampai lampu Led Indikator SGF menyala dan display menunjuk seperti dibawah ini :

b) Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini ;

RESETSTEP

n x 1 s 0 0 0

1 s

PROGRAM

1 0 0 0

c) Kemudian tekan push botton PROGRAM kira kira 5 detik sehingga display menunjuk seperti gambar dibawah

d) Kemudian tekan push botton PROGRAM 1 kali sehingga display menunjuk seperti gambar dibawah ini

e) Kemudian tekan push botton PROGRAM kira kira 1detik,sehingga display menunjuk seperti dbawah ini

5 s

PROGRAM

1 0 0 0

1x

PROGRAM

1 01

SGF 1 / 1 = 0

1s

PROGRAM

1 02

SGF 1 / 2 = 0

1s

PROGRAM

1 03

SGF 1 / 3 = 0

f) Kemudian tekan push botton PROGRAM kira kira 1 detik,sehingga display menunjuk seperti dibawah ini

Selanjutnya lakukan seperti program diatas untuk program selanjutnya :

SGF1/4 = 1 Bila dioperasikan sebagai back up ( Breaker Failure protection = CBF) SGF 1/4 = 0 Bila tidak dioperasikan sebagai back up (CBF) SGF 1/5 = 1 Bila dipakai sebagai proteksi terhadap inrush SGF 1/5 = 0 bila tidak dipakai SGF 1/6 = 0 SGF 1/7 = 0 SGF 1/8 = 0 Catatan : Bila menghendaki perubahan misalnya dari posisi SGF1/4=0 menjadi SGF1/4=1

Catatan : Bila menghendaki perubahan misalnya dari posisi SGF1/4=0 menjadi SGF1/4=1 Caranya : Tekan push botton STEP/RESET 1 kali sehingga perubahan display menjadi seperti dibawah ini

1X

STEPRESET

1 141 04

IBA DOK

Setelah pemrograman SGF1/1 s/d SGF1/8 selesai, maka dilakukanpenyimpanan . Dengan posisi SGF1/1 s/d SGF1/8 semuanya = 0 maka cara penyimpanannya adalah sbb:- Tekan push botton PROGRAM kira kira 5 detik, sehingga display menunjuk seperti gambar dibawah

5s

PROGRAM

1 0 0 0Merupakan total( checksum dari SGF )

- tekan push botton STEP/RESET dan PROGRAM secara bersamaan sehingga display menunjuk seperti gambar dibawah

PROGRAM

STEP/RESET

1 - - -1 0 0 0

Artinya semua dataYelah disimpan

2. SGF2 Untuk pemrograman SGF2 disetting sebagai berikut : - SGF2/1 s/d SGF2/4 diset = 1 ( reset secara manual ) - SGF2/5 diset = 0 ( I >> dioperasikan ) - SGF2/6 diset = 0 ( Io >> dioperasikan ) - SGF2/7 diset = 0 ( I >> tidak dipakai recloser ) - SGF2/8 diset = 0 ( Io >> tidak dipakai recloser )

Checksum = 15

3. SGB ( Switch Group for Blocking ) Setelah pemrograman SGF selesai, kemudian tekan push botton

STEP/RESET sehingga lampu LED SGF padam dan lampu LED SGB menyala/

Kemudian lakukan pemrograman / setting untuk SGB , caranya sama seperti pemrograman pada SGF.

Dalam hal ini program SGB 1/1 s/d SGB1/8 di set = 0 Checksum = 0 ( baca buku petunjuk / instruction manual )

4. SGR ( Switch Group of Relay Configuration ) Setelah pemrogram SGB selesai , kemudian kita tekan push

botton STEP/RESET sehingga lampu LED SGB padam dan lampu LED SGR menyala.

4. SGR ( Switch Group of Relay Configuration ) Setelah pemrogram SGB selesai , kemudian kita tekan push

botton STEP/RESET sehingga lampu LED SGB padam dan lampu LED SGR menyala.

Kemudian lakukan pemrograman ( setting ) untuk SGR caranya sama seperti pemrograman pada SGF.

Dalam hal ini program SGR diset sebagai berikut : - SGR 1/1 s/d SGR 1/8 di set = 1 checksum = 255 - SGR 2/1 s/d SGR 2/8 di set = 0 checksum = 0 - SGR 3/1 s/d SGR 3/8 di set = 0 checksum = 0

5. CARA PEMROGRAMAN ( SETTING ) I > / I >> / Io > / Io >> / t > / t >> / to > / to >> 5.1. Setting I > : misalnya Iset = 1,05 x In Caranya sebagai berikut : a. Tekan push botton STEP/RESET kira kira 5detik sehingga

lampu Led I > menyala dan display menunjuk seperti dibawah ini .

STEP/RESET

0. 8 05s

b. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini .

PROGRAM

1s 0. 8 01

PROGRAM

1s

c. Kemudian tekan push botton PROGRAM kira kira 5 detik sehingga display menunjuk seperti dibawah ini.

PROGRAM

1 0. 8 05s

0. 81 0

d. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini.

e. Kemudian tekan push botton STEP/RESET 5 kali sehingga display menunjuk seperti dibawah ini.

STEP/RESET

5x0. 81 5

f. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini.

PROGRAM

1s0. 81 5

g. Kemudian tekan push botton STEP/RESET kira kira 2 kali sehingga display menunjuk seperti dibawah ini.

STEP/RESET

2x0. 01 5

h. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini.

PROGRAM

1s0. 01 5

i. Kemudian tekan push botton STEP/RESET kira kira 1 kali sehingga display menunjuk seperti dibawah ini.

STEP/RESET

1x1. 01 5

j. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini.

PROGRAM

1s 1. 01 5

k. Kemudian bila kita menghendaki perubahan titik desimal (memindahkan titik desimal), maka tekan push botton STEP/RESET sesuai keinginan kita.

l. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini.

1 1. 0 5

PROGRAM

1s

m. Kemudian tekan push botton PROGRAM dan STEP /RESET secara bersamaan, sehingga display menunjuk seperti dibawah ini.

PROGRAM

1. 0 51

STEP/RESET

- - -1

Artinya semua data disimpan

Catatan :- Jika menghendaki untuk pemrograman ( setting ) STAGE 2 ,

Setelah melakukan langkah m) , kemudian tekan push botton PROGRAM kira kira 5 detik, sehingga display menunjuk seperti dibawah ini .

1 1. 0 5

PROGRAM

5s

- Kemudian tekan push botton STEP/RESET kira kira 1 detik (untuk merubah angka stage ) sehingga display menunjuk seperti dibawah ini.

2 1. 0 5

STEP/REET

1s

-Setelah itu lakukan seperti langkah langkah (prosedur ) d) s/d m)

5.2. Setting I >> / t > / t >> / Io > / Io >> / to > / to >> lakukan pemrograman seperti cara Setting I > .